SYLVANIA Heaters are now branded OSRAM Heaters. Same high quality products and service.
Air Heater Energy Requirement:kW = SCFM x (Texit – Tinlet) / 2500________________________________________Temperature Conversions:°F = 9/5 (°C) + 32°C = 5/9 (°F – 32)________________________________________Air Flow Conversions:SCFM = SCFH / 60 = SLPM / 28.3SLPM = SCFH / 2.12SCMH = SCFH / 35.3SCFM = (Pounds of Air Per Minute) / (.080 lbs/ft3)SCFM = Standard Cubic Feet per MinuteSCFH = Standard Cubic Feet per HourSLPM = Standard Liters per MinuteSCMH = Standard Cubic Meters per Hour
Wye Configuration________________________________________Single Phase Wiring:V = I x R (Volts = Amps x Ohms)I = W / V (Amps = Watts / Volts) W = V2/R (Watts = (Volts x Volts) / Ohms)________________________________________Three Phase Wiring:Delta Configuration:R = R1 = R2 = R3Wdelta = 3(VL2)/RWdelta = 1.73 x VL x ILIP = IL/1.73VP = VLWye Configuration:R = R1 = R2 = R3Wwye = (VL2)/R = 3(VP2)/RWwye = 1.73 x VL x IPIP = ILVP = VL/1.73
Register to receive OSRAM SYLVANIA newsletters and communications for the latest news, deals, and product information!
Copyright © 2013, OSRAM SYLVANIA